It should fully complies and meets HTM02-01 standards or ISO standards only. Country of origin certificate must be submitted. . It should be duly CE marked and comply with 93/42/EEC Medical Devices-General. It shall be CE marked with the notified body number specified. The system shall be provided as factory assembled configurations. The pendant frame shall be constructed from extruded aluminium alloy 6063 T6. The end caps should replicate the profile of the vertical head. The aluminium extrusions used to contrast the pendant shall be of approximate wall thickness not less than 3.5 mm. The external surfaces should be antibacterial paint which ensures 100 percentage shield against infectious agent. The pendant lids shall be removable to allow access to the aluminium sections. Segregation shall be provided within the side sections to ensure that services are not effected. It should be swivelling 0-330 degree with load capacity 180Kg. It should have Ceiling single support adaptable to false ceiling Hmax 800mm. It should have vertical column H1000mm. It should have pre wired 10 multipin 6/16amp electrical sockets of Indian standards. It should have 2 data sockets of Indian standards. It should have one shelf bioclean made of solid material for ceiling pendant with handle and 2 rails (L470xW450mm) (capacity load 40Kg). It should have Swivelling vertical pole stainless steel telescopic H=1000mm D25 for accessories with IV stand with4 hooks (capacity load 30Kg. It should have pre piped 6 gas outlet points gas outlet points with NIST connection and manometer. Gas Outlet Points (* 2 Oxygen, 1 N2O, 1 AGSS and 2 Vacuum) should fully complies and meets with the requirements of the UK DOH Health Technical Memorandum 02-01 (HTM 02-01) standards only. It shall be CE marked with the notified body number specified on it. It shall be provided with a copy of the certificate of origin. Terminal units shall have gas indexing geometry. Other gas specific indexing geometries are not acceptable. Terminal unit front fascia should be metal and it should be hundred percent metal. Gas specific components comprising the terminal unit second fix shall be manufactured from die-cast zinc alloy or similar hard wearing metal. Plastic components are not acceptable. Terminal units socket castings shall be permanently coated with a low friction fluoropolymer for maximum reliability and service life. The terminal unit socket die-casting shall incorporate a gas indexing pin to overcome the risk of loosening due to rough handling or abuse. The second fix socket shall incorporate a sheer-plane to safeguard the first fix and pipeline in the event of accidental damage or bed jacking. Gas specific components shall incorporate the gas identity marking permanently stamped or cast into the component surface. The first fix shall be all metal construction, with a brass base block and copper stub pipe. The first fix shall incorporate an integral check valve to enable servicing of the second fix and valve seals without isolation of the gas supply. Probe roller pins shall be manufactured from stainless steel. Wall mounted terminal units shall be provided with white ABS mounting box with matching fascia. The mounting box shall have smooth rounded corners to avoid the possibility of injury. A bezel shall be available to cover the plaster edge, provide a neat and easily to clean finish.